Duraplus Chimney Pipe Requirements & Tips
The following recommendations are intended as a general guideline to assist in the layout and selection of the chimney components needed for your installation. Always read and follow DuraVent Dura-Vent Installation instructions before installing your chimney system, found with the cap or support box. Installation instructions can be viewed on the products item page.
- The diameter of the chimney should match the outlet size of the appliance. An improperly sized chimney results in poor draft and excessive creosote formation.
- Measure the diameter of the appliance flue outlet. Select the chimney and either DVL or DuraBlack connector stovepipe with the same size diameter as the appliance flue outlet. For fireplace installations, refer to the sizing chart in the back of this catalog.
- Determine if the installation is a through-the-roof installation or a through-the-wall installation. A through-the-wall installation will require additional components (Wall Thimble, Tee w/ Cap, Tee Support, and Wall Straps).
- Install the chimney in the interior of the structure whenever possible. A cold exterior chimney will produce less draft and will generate more creosote.
- If possible, avoid offsets that serve to restrict the natural draft. A straight vertical installation is more efficient and less likely to develop
creosote. If an offset is required to avoid rafters or other obstructions, measure the horizontal distance required and the vertical height
available. Both 15° and 30° elbows are available. Elbows greater than
30° are not allowed in the United States. A maximum of two offsets in a single installation are permitted. Refer to the offset table in the back of
this catalog. At least one Elbow Strap is required for each offset. Elbow Straps ensure adequate support.
- Determine the minimum chimney height above the roof line. Building codes require a minimum of 3' above the roof penetration and at least
2' higher than any portion of a building within 10'. See figure 1. The termination cap is installed above that point.
- Measure the roof pitch. For example, a 6/12 pitch has a vertical rise of 6" over a horizontal distance of 12". Select the appropriate flashing.
- Determine the total length of chimney and stovepipe required for the installation. To calculate the installed per length of 6"-8"
DuraPlus chimney pipe, subtract 1 1⁄2" per joint. Subtract 1 1/4" per joint of DuraBlack stovepipe. Subtract 1 1/2" per joint of DVL stovepipe.
Minimum chimney height, at sea level of straight vertical chimney is
10' to 15' above the appliance outlet. Higher elevations, or the use of elbows or a tee, will require approximately 30% to 60% more height to
provide for an adequate draft.
- Be fire safe. Maintain at least 2" clearance to combustibles. Follow local building codes and have your chimney inspected by a